Sedimentation Process in water treatment
In this process, water is kept standstill in a large settling (clarifier ). Undissolved suspended solids are settled at bottom of the tank. the sediment deposited in this process is removal by a so Slow moving horizontal scrapper. This process is very slow. it takes long time to settle the suspended solids. Also total solid cannot be removed completely in this process. Addition of coagulates like alum makes the settling process faster. Poly electrolyte is also used for this. another important external treatment of water is Demineralization process . this process is used at large scale in modern power plant industries for softening the water . here we discussed the demineralization process in detail way :
Demineralization process :-
Demineralization is the Removal of dissolved ionic impurities that are present in water. Demineralized water is commonly produced by one or a combination of following process.
3. Thermal desalination
The method selected to produced Demineralized water depends on the quality of the influent water , the required quality of influent water , the availability of the resources such as regenerant chemicals , and waste water treatment and disposal requirement . The economics of the process that that produce acceptable effluent quality must be evaluated to determine the most cost effective method for a specific application.
Inorganic Removal is accomplished through the adsorption of contamination ions into a resin exchange medium. One ion is substituted for another on the charged surface of the medium that is usually a plastic resin. This type of surface is designed as either cationic or anionic negatively charged. The medium is saturated with exchangeable ions before the treatment operations.
The contaminant ions during ion exchange, replaced the regenerant ions because they are preferred by the exchange medium. When no ions are left to take the place of the contaminant ions, the medium is regenerated with a suitable solution that saturates the medium with the appropriate ions . Since there is a required down time, the regeneration cycles are done only once per day.
For resin exchange, capacity is expressed in terms of weight per unit volume of the resin used. Calculation of the breakthrough time for an ion exchange unit requires knowing the resin exchange capacity, influent contaminant concentration and the desired effluent quality.
READ MORE ARTICLES RELATED TO WATER TREATMENT
- INTRODUCTION AND WORKING PRINCIPAL OF REVERSE OSMOSIS
- Boiler Water analysis and it’s importance
- WATER IMPURITIES AND THEIR CLASSIFICATION
- Water impurities and their harmful effects on boiler
- Filtration process in water treatment
- | Sedimentation Process in water treatment
- WORKING PRINCIPAL OF MIX BED
Advantage of D.M plant
> Ion exchange can be used with fluctuating flow rates
> Makes effluent contamination impossible
> Resin are available in large varieties from supplier’s and each resin is effective in removing specific contamination.
IF YOU LIKE THIS POST ” Sedimentation Process in water treatment” PLEASE LIKE , SHARE AND YOU COMMENTS IS VERY VALUABLE SO PLEASE GIVE YOUR SUGGESTIONS IN COMMENT BOX please read once time if any mistake you find in this artical please suggest me through comment box or if this website contains all original article which are written by me if any article on this site find copyrighted please inform me through at firstname.lastname@example.org……..THANK’S
Heii all power engineers myself joginder chauhan . i am the founder of my website www.askpowerplant.com. i am also a power engineer and having the more than 5 year experience in the field of power sectors during this time period i learn about different power technology like AFBC , CFBC , TRAVELLING GRATE , PULSATING GREAT , PF BOILER , WHRS and many more things . my motive from this site sharing my power sector knowledge each and everyone who belonging to this field , in this website i share information related to boiler operation , boiler maintenance , turbine operation & maintenance , boiler & turbine question answer , D.M plant , and all topic related to power plant sector please join this website for latest updation regarding power plant ………..thanks ( JOGINDER CHAUHAN )