TURBINE THRUST BEARING AND IT’S FUNCTION
The thrust bearing consists of Babbitt metal lined, stationary shoes that run against the rotor thrust runner. Shoes on both sides of the runner prevent movement in either axial direction. Journal bearing are used to take radial load of the shaft. But it can’t take axial load. Shaft is permitted to float to both axial directions. but the axial float is restricted to certain limit. Excessive axial shift may damage rotation and fixed parts. For this thrust bearing are provided.
Thrust bearing consists of series of sector- shaped shoes or pads fixed on pivots and arranged in a circle around the shaft collar. Each shoe is free to tilt about a pivot. Normally, the pivot takes the form of a hardened spherical surface inserted behind each shoe. The shoe is free to tip in both circumferential and radial directions. This allows accommodation of any misalignment that may exist between the shoes and the thrust runner. When the runner is stationary, the shoes are parallel to the runner Oil pressure causes the pad to tilts slightly, building a wedge of pressurized fluid between the shoe and the collar surface. This tilting pad tilts and remains in a particular position depending upon the bearing load and speed. Wedge -shaped regions of oil are created inside the bearing between the pads and rotating collar. Which supports the applied thrust and eliminate metal-on-metal contact .
Each pad is free to tilt so that it creates a self sustaining hydrodynamic oil film. Like journal film like journal bearing. The face of these pads is babbitted. Pads are arranged around the protected collar of the shaft. Lubrication oil supplied to created oil film between shaft collar and bearing pad. The pads are fitted with temperature sensors (RTD’s)
normally two sets of thrust bearing are provided in front bearing pedestal at both side of the shaft collar. The tilting-shoe type of thrust bearing is capable of carrying the greater load of the two thrust-bearing types.
IF YOU LIKE THIS POST ” TURBINE THRUST BEARING AND IT’S FUNCTION” PLEASE LIKE , SHARE AND YOU COMMENTS IS VERY VALUABLE SO PLEASE GIVE YOUR SUGGESTIONS IN COMMENT BOX please read once time if any mistake you find in this artical please suggest me through comment box or if this website contains all original article which are written by me if any article on this site find copyrighted please inform me through at [email protected]……..THANK’S
Heii all power engineers myself joginder chauhan . i am the founder of my website www.askpowerplant.com. i am also a power engineer and having the more than 5 year experience in the field of power sectors during this time period i learn about different power technology like AFBC , CFBC , TRAVELLING GRATE , PULSATING GREAT , PF BOILER , WHRS and many more things . my motive from this site sharing my power sector knowledge each and everyone who belonging to this field , in this website i share information related to boiler operation , boiler maintenance , turbine operation & maintenance , boiler & turbine question answer , D.M plant , and all topic related to power plant sector please join this website for latest updation regarding power plant ………..thanks ( JOGINDER CHAUHAN )